Discontinued by Manufacturer
SE8300 Series room controllers are used for Low Voltage Fan Coil Unit control. The room controllers rated supply voltage range is 24 to 28V AC at 50 or 60Hz +/-15%. The rated current is 4A. The device consumption is up to 12VA. The room controller is colored white and is equiped with a communication port that uses BACnet MS/TP protocol and a PIR sensor. Its Room and Outdoor Air Temperature Display Range is between -40 and 50 oC. The measurement accuracy is +/- 0.5%. The temperature setting range is 12 to 37.5oC for cooling and 4.5 to 32 oC for heating. The room controller is equiped with 2 digital inputs, 5 analog inputs (5 to 10V), 4 analog outputs, and 5 digital outputs. The analog output voltage is 0 to 10V DC at < 5mA into > 2 kOhm resistance. The digital output rating is 28V AC 50 or 60 Hz, 0.3A, 1.5A inrush current. The product follows the following standards: IEC 61326-1: 2005, FCC part 15 subpart C, RSS 210 issue 8, FCC part 15 subpart B, ICES-003, EN 60950-1: 2006/A2, EN 60950-1: 2013, ETSI EN 301 489-1: v1.9.2. The product follows the directives: 2014/30/EU - electromagnetic compatibility, 2014/35/EU - low voltage directive, 2014/53/EU - radio equipment directive. The ambient air temperature for operation is between 0 and 50oC. The relative humidity for operating or storage is between 0 and 75% non condensing. The humidity reading range is 10 to 90% RH non-condensing.